|Communication HMI BEIJER/PLC AB (ATHERNETIP)
|Page 1 of 1|
|Author:||abdelhak [ Thu Jul 20, 2017 2:30 am ]|
|Post subject:||Communication HMI BEIJER/PLC AB (ATHERNETIP)|
I want to connect a HMI BEIJER IX T10A with a plc Allen bradley, but currently HMI is already connected with a plc Mitsubishi.
The reason I want to add an AB plc is because all Mitsibishi plc inputs are full.
Is what I can connect 2 plc with HMI Beijer, even though the Mitsubishi protolcol is serial and plc AB which is with ethernet / IP.
WHAT IS THE PARAMETERS I MUST DO ON BEIJER AND PLC. ??
Thank you for your answers.
have a good day
|Author:||Russ C. [ Mon Apr 02, 2018 2:13 pm ]|
|Post subject:||Re: Communication HMI BEIJER/PLC AB (ATHERNETIP)|
You should be able to add multiple controllers to the project in iX Developer as needed.
You can access the controllers via the Tags page and clicking the Controllers tab. From there click Add and select your new controller. With the new controller selected, you can configure settings for that controller under the Settings button. If you need more clarification on the settings for that specific controller, click the Help button the settings window and the help file will go into more detail about things like addressing and serial communication pin outs.
|Page 1 of 1||All times are UTC - 7 hours [ DST ]|
|Powered by phpBB © 2000, 2002, 2005, 2007 phpBB Group